Secure a good building ventilation and working environment with optimized machine hall ventilation system.
Modifications to existing machine hall ventilation systems can be done by installing additional ventilation units, both supply and exhaust air units, locating them in positions where they give the best benefit.
The Main benefits:
Normally such new supply air units including needed heating coils are connected to the existing heat recovery circulation water system. Additionally, needed machine hall exhaust air units are to be located as close to the heat and moisture source as possible.
The paper making process with all its moisture and heat loads is putting high demands not only on the process ventilation equipment but also on the general machine hall ventilation solutions. The exhaust air system connected to the closed hood covering the dryer section will take care of the major part of the heat and humidity load coming from the process.
In addition to this local process exhausts being installed in different parts of the production line, like forming section and process pulper exhausts and mist removal systems in connection to HP water showers will further decrease the heat and humidity loads.
To balance the amount of air being exhausted from the process and normally blown outside, the building must be equipped with an appropriate machine hall ventilation system, dimensioned for a good overall balance both during cold winter and warm summer periods.
In rebuild projects of existing paper machines attention is also to be paid to possible changes in the air balance of the machine hall building. Additions in the process exhausts should always be countered by additions also in the machine hall ventilation equipment. This to guarantee an adequate balance also after the rebuild.
Paper Machine Vacuum Blower Systems Solutions RunEco
Environmentally friendly and energy efficient, RunEco Vacuum System provides a reliable, completely water free vacuum solution that is ideal for industrial applications.